35 Foot 3/8 LL 1 1/8 SL Line Set
Model: Alpine 61880351 (Item No. 699330)
This Alpine 35 Foot 3/8 LL 1 1/8 SL Standard Split System Line Set 61880351 has some cosmetic damage incurred during shipping. Line set was returned with tears in the insulation. For detailed photos please click 'See Additional Images' above. This Alpine 35 Foot 3/8 LL 1 1/8 SL Standard Split System Line Set 61880351 meets the full manufacturer's specifications, comes with the full manufacturer's warranty, and includes Alpine's premium guarantee.
For product specs and photographs of product in its original condition, click here.
Line sets are the copper lines which connect an outdoor condensing unit/heat pump to an inside air handler or evaporator coil. Line sets are available in different lengths and diameters to fit most applications. Below are tips to help select the proper size to match the needs of your system.
- The 1 1/8 suction lines will typically be connected to outdoor units and evaporator coils with a 7/8 suction line connection. It is recommended that you include two JMF CF118-78 Kits with each 1 1/8 line set that you order. the JMF CF118-78 Kit consists of a 1 1/8 to 7/8 reducer with female connections and a 7/8 stub male fitting. This kit will allow the 1 1/8 line sets to be connected to 7/8 suction line fittings.
- When purchasing refrigeration lines, measure the length of line set needed to connect your outdoor condenser to the indoor forced air equipment. Based on that length, the correct size diameter line set can be selected which will ensure your system meets the listed SEER rating and capacity. Once you have accurately measured the length needed, use our chart below to find the diameter best for your system.
- When feeding a new line set through the wall, it is typically easier to feed the lines “out” from the inside of the home rather than “in” from the outside. This will also minimize any damage to the suction line insulation when feeding it through the wall. It is always advisable to slowly roll the lines open to avoid putting crimps in the lines. If you encounter a tight radius bend, cut the suction line and braze a 90° or 45° fitting to avoid kinking the flexible tube. The installation DVD includes more tips on running line sets.
- When sweating the line set to the equipment or fittings use an oxygen/acetylene torch (preferred since it is hottest) or MAPP gas torch and high silver content brazing rods to achieve a proper brazed connection. Propane gas or MAPP/PRO torches should *not* be used, since they will not generate enough heat to make a good connection. When brazing pipes into air conditioning condenser or heat pump, first tie a wet rag around the service valves to dissipate heat. If this isn't done, there are small rubber O-rings in the valves which can melt and cause refrigerant leaks. If you aren't familiar with using a torch, for your safety have your air conditioning contractor perform this task for you. Wear proper eye and hand protection when operating a torch.
- Once all of the line set connections have been brazed, a vacuum must be pulled on the system to evacuate the lines. The manufacturer's installation instructions describe the system evacuation process. If your system operates on R-22, then by law you must have an HVAC technician do this part of the job for you.